In today's article I walk you through how to set or change a CompactLogix processor's Ethernet address through its USB port using RSLinx Classic.
Step 1) Confirm your RSLinx RSWho window browses your CompactLogix via the USB driver
Open RSLinx and check to be sure your CompactLogix is showing up under the USB driver as shown below:
NOTE: If you would like to know how to setup an RSLinx driver to communicate to a CompactLogix processor using a USB connection, see our previous article HERE.
Step 2) Select the CompactLogix processor
The next step is to select the CompactLogix processor under the USB driver as shown below:
Step 3) Right click on the CompactLogix and select Module Configuration
Right click on the CompactLogix processor and select “Module Configuration” from the menu as shown below:
Step 4) Select the “Port Configuration” tab
In the popup window select the “Port Configuration” tab:
Step 5) Enter in a new Ethernet address and insure “Static” is selected
Now you can enter in an Ethernet address for your CompactLogix's Ethernet port. Also be sure “Static” is selected, and then click on OK:
Step 6) Accept Configuration
The final step is to accept the configuration by clicking on “Yes,” after which your CompactLogix will have the Ethernet address you entered above:
NOTE: Watch me run through the above steps in today's video episode of The Automation Minute!
I hope the above article on how to set or change a CompactLogix's Ethernet address through its USB port using RSLinx was helpful.
If you have any questions or comments, please feel free to share them with us by clicking on the “post a comment or question” link below.
Sponsor and Advertise: Get your product or service in front of our 70K followers while also supporting independent automation journalism by sponsoring or advertising with us! Learn more in our Media Guide here, or contact us using this form or by calling our office at 413-749-4300.
- ControlLogix and Studio 5000 Update from Rockwell Automation (P114) - August 10, 2022
- Get Data From MicroLogix via Modbus and NET-AIC? - August 8, 2022
- Can You Manually Reset A PLC Timer? - August 5, 2022