NOTE: While this procedure works for older models as well, to see the a procedure written for the original PanelView Plus CE / VersaView CE click HERE:
So you have a PanelView Plus 7 and want to Enable and Use VNC to remotely view and or control it?
Well in today's article I'll show you step-by-step how to use the PanelView Plus Configuration Menu to do just that.
Step 1) Power on your PanelView Plus and return to the main configuration menu as shown below:
Note: If you don't know how to get back to the main configuration menu, check out my previous article on that topic:
Step 2) Select Exit from the main menu, and if prompted enter in the Desktop Access password. Next select Start, Settings, and Control Panel:
Step 3) Now in the Control Panel select Services on the bottom left:
Step 4) Next in the Services screen select VNC Server to turn it on and make it change from Red to Green. Then select Done to close the Services screen:
Step 5) Now select Server Config from the bottom left of the Control Panel:
Step 6) Here select the VNC Server Tab and make any changes you need to make to the configuration.
Note: It's recommended to enable security along with requiring a password, especially for full control applications:
Step 7) When done select the OK button on the top right of the Network Server Configuration window, and then Yes if prompted to restart services:
Step 8) Now on your PC open an VNC client application like TightVNC and enter in your PanelView Plus 7's Ethernet IP address and then Connect to it:
Step 9) Next, if a password is required enter it here and select OK:
Step 10) After connecting, you should see a copy of your PanelView Plus 7's display inside of your VNC client. If you allowed full control, you should be able to control your PanelView Plus 7 remote from your VNC client as well:
Question: Did you Find this article helpful? If so, please share it with co-workers and colleagues, and for more articles about the PanelView Plus click on the link below:
You can watch a video of the above procedure in the below video(s):
I hope you found this article helpful. If you have any questions please feel free to post them at Forums.TheAutomationBlog.com
Shawn began sharing automation news and know-how online in 1996 when he launched his first BBS. Then in 1999 he moved to the internet launching ShawnMichael.com, which he later renamed ShawnMTierney.com. In 2013 he moved his automation efforts to a new website, TheAutomationBlog.com, which has since become the most popular independent industrial automation blog on the web.
Latest posts by Shawn Tierney (see all)
- How To Add Profinet I/O & Drives To S7-1500 (video) - October 8, 2019
- Mitsubishi iQ-R PLC Overview - October 3, 2019
- Mitsubishi iQ-F FX-5 PLC Overview - October 2, 2019
Click HERE to scroll down to view or leave comments