Why is the PanelView Plus “Goto Config Mode” white box missing on boot? Why doesn't pressing F1 on boot bring me to the PanelView Plus configuration mode?
Yesterday we discussed how to get into the “Configuration Mode” of a PanelView Plus, and we learned the easiest way to do so was to either put a “Goto Config” button in your FactoryTalk View Machine Edition (ViewME) project, or intterupt the boot process of the terminal by pressing the “White Box” in the lower left corner of a touch screen unit, or the “F1 Key” on a keypad unit.
But what do you do when the “White Box” doesn't show up, or the “F1 key” doesn't work?
There's two reasons why this may be happening:
First, it could be your PanelView Plus has a firmware version prior to 3.20.09. If that's the case, the firmware loaded in your terminal predates the inclusion of the “White Box” and “F1” power-up auto load interrupt. In these cases I highly recommend backing up all the .mer files on your PanelView Plus, and well as recording all your network and communication settings, and then flashing your unit up to the latest firmware available for your PVPlus, which would be version 5.1+.
You may also have to visit the Rockwell Software Downloads Page to find a copy of the 3.0 to 3.1 firmware migration files as last time I checked 3.0 first has to be migrated to 3.1 before it can be migrated to any other version
The second reason you may not see the “White Box,” or the “F1 Key” does not work to interrupt the boot process could be because you have a PanelView Plus 6 with firmware 6.0. It's quite an annoyance that version 6.0 of the PVPlus 6 did not have this feature which so many people rely on, and to bring the feature back you'll need to first flash your PanelView Plus 6 to version 6.1. And just like when flashing a PanelView Plus, before you do so you should back up all your .mer files which are on the terminal, and well as record all the terminal's network and communication settings.
Once your PVPlus 6 terminal is flashed to 6.1 you still need to enable the “White Box” / “F1 Key” functionality. To do this you must exit “Configuration Mode” to get to the “Windows CE” desktop. And to do that you'll need to know the password, which by default is “password.”
Once in Windows CE, open the Control Panel, chose “System,” then “Start-up Options,” then “Boot Option,” and select “Detect safe mode request at startup.” It's quite a few steps, but it does bring back the “White Box” and “F1 Key” boot-up functionality, which I have to say is much better than the option provided in version 6.0 required plugging in a USB keyboard into the back of the PVPlus 6.
If you have anything you would like to add to the above, or have any questions on this information, please feel free to use the “Leave a reply” form below to comment on this article.
Need personalized help? For as little as $25 per month you can get direct access to ask me Rockwell PLC, HMI, and SCADA questions! Learn the details at Patreon.com/Automation