In this week's episode of The Automation Show, I cover how to use View Studio to create and download a PanelView Plus program to read data from a ControlLogix, SLC-5/04 and PLC-5 over a Data Highway Plus network:
For more information, check out the “Show Notes” located below the video.
The Automation Show, Episode 35 Show Notes:
Support our site and get early access to our videos, free downloads and more!
You can now support our site with a small monthly pledge and in turn receive instant rewards! To find out more visit https://Patreon.com/Automation.
You can also purchase the entire season of The Automation Show for a one time donation of $25 at https://vimeo.com/ondemand/theautomationshow.
Thanks in advanced for your support!
Vendors: Would you like your product featured on the Show, Podcast, and Blog? If you would, please contact me at: https://theautomationblog.com/contact
Enjoy the benefits of membership! Insider news, rewards, & more: Patreon.com/automation
If you enjoyed my article, you may like my courses at TheAutomationSchool.com
Have a question on this topic? Click here to scroll down to the comment link
Have a news tip? Share it with us here
Latest posts by Shawn Tierney (see all)
- RSView32 to SLC-5/04 & PLC-5 over DH Plus via Ethernet and 1756 Gateway (S36) - March 27, 2020
- Mitsubishi VFD Product Overview (P51) - March 26, 2020
- Insider News for February 2020 (Patron Only) - March 18, 2020
Click HERE to scroll down to view or leave comments
- I got a Panelview 1250. I uploaded to the laptop using the transfer utility. I proceeded to add to the panelview a new function I’m needing. The new value has already been made on the compaqlogix.
However, there are no communication paths listed. The path short cuts are listed, but there e path they point is not showing up. Says it doesn’t exist.
I can manually find the path. However, if I do that, will it jack up the interface when download it back to the panelview?Good morning @rwcanary,
Could be several reasons why you're not seeing communication paths based on your SW and HW versions, and which tab is missing the paths. But worse case you can pull them up on the PanelView Plus itself.
That said, I'd be surprised if you don't see the communications paths in the Runtime/Target Tab if the Application Manager allowed you to recover the project from the version 5.0 or greater .MER file on the PVP?
(for those interested I talk more about that here: https://theautomationblog.com/how-to-edit-a-panelview-plus-viewme-mer-runtime-file/)
I would expect the Design/Local tab to be empty if you've never created a project in ViewStudio ME on your current PC, since the Local Tab is your PC's setup.
Instructor at www.TheAutomationSchool.comThanks Shawn,
Further investigating. I see the paths have been configured in the runtime tab. If I high light the shortcut (IE. Palletizer) it gives an error on the lower frame border say the path "compaq blah blah blah.Line_3_5" cannot be found.
The design/Local is empty. Do I need to create comm paths in the design/local?
I wondering if perhaps it makes a difference on how (or where I am connected) into the ethernet network. Theoretically it should not matter.
You mentioned "But worse case you can pull them up on the PanelView Plus itself.", I went through the Panelview, however, I did not see anything to tell that information. Where would it listed?Good morning @rwcanary,
Setup the Design/Local paths for your shortcuts only if you wish to test run the application on your PC - it also does not have to match the Target/Runtime tab as I show in my PanelView Plus videos.
I do walk through how to find the shortcut paths on the PanelView Plus itself in the below article:
Hope this helps,