So you have a PanelView 550 Series A with a “hard to find” backlight that's failed and needs replacement?
Well, the good news is that there are several third parties that have come out with an LED version of the lamp that's inexpensive, easy to install, and runs much cooler that the original.
If fact, I recently purchased one to install in a friend's terminal, and in this article I'll share some pictures of the replacement process.
Step 1) Disconnect power from your PanelView 550, then remove the back cover and failed lamp, if it's still installed (below the cover and lamp have already been removed:)
Step 3) Remove the replacement LED lamp from the packaging (you can purchase it here).
Step 4) If you have concerns about the lamp becoming loose, install the anchors:
Step 5) Slide open end of the LED lamp as far in on the fiber bundle as you can:
Step 7) Slide the lamp into the metal lamp holder clip:
Step 8) If you installed the anchors in step 6, now go ahead and install the tie wraps (not shown).
Step 9) Plug the lamp connector into the PanelView 500 lamp socket.
NOTE: Since there are no polarity markings on the socket, you have a 50/50 chance of getting the polarity correct. With my PanelView 550, the correct polarity had the Red wire on top:)
If you'd like to watch a video demonstration of the above, check out Episode 21 of The Automation Minute Season 4 below:
I hope you've found the above information above about replacing the lamp on a PanelView 550 helpful.
If you have any questions, or would like to comment on the above article, please feel free to click on the “post a comment or question” link below.
You can also become a Patron to support my work at Patreon.com/Automation and in return receive free downloads of my sample, videos, and blog articles.
Enjoy the benefits of membership! Patreon.com/automation
Check out my affordable courses: TheAutomationSchool.com
Ask me questions by clicking here to go to the comments link
Have an industrial automation news tip? Share it with us here
- First Look: Distance Sensor with Analog Out and IO-Link, Pepperl+Fuchs OMT600-R200-IEP-IO-V1-L - November 24, 2020
- Automation Fair: My Session Picks (so far) - November 19, 2020
- Automation Fair Virtual Networking Tour - November 17, 2020
Click HERE to scroll down to view or leave comments