I'm not sure I can connect to my PanelView Plus 600 at work to edit its program using Ethernet because I'm not an admin on my PC and can't change my Ethernet settings from DHCP.
Can I use USB or go through my CompactLogix's USB port to program and edit my PVPlus program?
To start, please know you can connect to any PanelView Plus HMI over Serial, Ethernet, or both Serial and Ethernet depending on which ports your model has.
The PanelView Plus 6 and 7 also include the aility to upload and download to them via USB. For more information about that, check out the below Rockwell tech note:
However, these connections are for using the “Transfer Utility” to either upload or download .MER runtime files as discussed and demonstrated in the course.
That said, you can't edit the PanelView Plus online like you can a PLC or PAC, and I don't know of a way to upload or download to the PanelView Plus through the USB Port on a CompactLogix, but I've also never tried this (however I'm not too confident it would work…)
As far as your Ethernet connection, as long as the DHCP server your connected to puts you one the same subnet at the PVPlus, or puts you on a subnet with a router connecting your network to the PVPlus's network, then you should be able to connect.
As far as serial goes, it's often not an option because most developers do not add the serial driver to the Target/Runtime tab, so it typically isn't enabled on the PVPlus and therefore can't be used.
If it is enabled, or if you reset the PVPlus comms to default to enable it, you'll find it's rather slow, so much so that I avoid using serial and instead use removable storage like a USB Flash drive or CompactFlash/SD card.
You can even write auto run scripts to copy the files when you insert your removable memory, perfect for cases when you're locked out of the Configuration Menu. For more on that, check out the below article:
Hope this helps!
Enjoy the benefits of membership! Patreon.com/automation
Check out my affordable courses: TheAutomationSchool.com
Ask me questions by clicking here to go to the comments link
Have an industrial automation news tip? Share it with us here
- First Look: Distance Sensor with Analog Out and IO-Link, Pepperl+Fuchs OMT600-R200-IEP-IO-V1-L - November 24, 2020
- Automation Fair: My Session Picks (so far) - November 19, 2020
- Automation Fair Virtual Networking Tour - November 17, 2020
Click HERE to scroll down to view or leave comments
Note: All students who purchase my courses are encouraged to ask questions related to the content covered in those courses. Digital customers may ask questions in the related lesson's discussion area on the site they purchased the course from (i.e. Vimeo.com, etc) For DVD customers who register, I'll soon be opening a new Q & A section on TheAutomationSchool.com.