Recently I’ve been running into the perception that Rockwell’s new 5370 CompactLogix controllers have the ability to control less I/O than previous models.
To address this question, today we’ll take a look at the 1769-L32E versus the 1769-L33ER to see which one of these CompactLogix processors can control the most I/O.
L32E vs. L33ER: Local I/O
L33ER: Supports sixteen local I/O modules.
As far as local I/O goes, the L32E and L33ER tie as each support sixteen 1769 local expansion I/O modules.
L32E vs. L33ER: Remote Ethernet Racks of Discrete I/O
Using Rockwell’s Ethernet IP Capacity tool (more on this tool here,) we are able to add thirty two remote racks of Point I/O (or Flex I/O) to the L32E.
L32E: Thirty two remote racks of discrete I/O
L33ER: Thirty two remote racks of discrete I/O
As far as the number of remote racks of discrete I/O, the L32E and L33ER tie again since each support thirty two remote racks of I/O.
L32E vs. L33ER: Remote Ethernet Analog Modules
This time we’ll start with the L33ER and the current configuration of thirty two remote Ethernet racks of I/O.
Using this configuration we find we can add up to six analog modules (at an eighty millisecond update rate) to each of the thirty two racks and still be within this processor’s limit.
L33ER: Thirty two racks with six analog modules each
L32E: Four racks with six analog modules each
Winner: L33ER by a very wide margin
As far as which processor supports the most analog modules, the L33ER and it’s expanded number of connections supports many times more analog modules in remote Ethernet I/O racks.
L32E vs. L33ER: Remote Ethernet Variable Frequency Drives
With that in mind, let’s compare the number of VFD’s supported on Ethernet by each processor.
L32E: Thirty two VFDs
L33ER: Thirty two VFDs
Bonus Round: Number of HMI’s supported
While not I/O, I thought it would be helpful to also compare the number of HMI’s the L32E and L33ER support.
Before we begin though, I wanted to share this warning from the Ethernet IP Capacity Tool that pops up when adding HMI’s:
Here we can see it theoretically supports up to 51 PanelView Plus HMI’s when the HMI project has 200 tags updating at 250ms.
However, when we select the same HMI configuration for the L32E, we find it can theorectically only support six PanelView Plus units.
L33ER: Fifty one PanelView Plus HMI’s
L32E: Six PanelView Plus HMIs
Winner: The L33ER by a very wide margin
After reviewing the I/O capabilities of both the 1769-L32E and 1769-L33ER above, it’s quite clear that the newer L33ER supports the same number of Ethernet I/O racks.
But, in those racks it can support many more analog modules, as well as theoretically support a substantially larger number of HMIs at the same time.
So with that said, the L33ER is the clear winner of this VERSUS competition.
I hope you’ve enjoyed this article comparing the amount of I/O supported by the L32E and L33ER.
If you have any comments, questions, corrections or suggesting please feel welcome to leave them with us by filling in the “post a comment or question” link below.
Until next time, Peace ✌️
Shawn M Tierney
Technology Enthusiast & Content Creator
If you found this content helpful, consider buying me a coffee here.
- Rader Level Measurement: Is 80GHz Right For Your Application? (P194) - February 28, 2024
- February 22 News on Sensors, 5G Routers, Profinet Gateways, Edge IPCs, Robots and Ai in 2024 & more (N169) - February 22, 2024
- Siemens Scalable Machine-mount I/O (P193) - February 21, 2024