In today's article I'll show you how to use Rockwell's new Ethernet/IP Capacity Tool.
The replacement for Rockwell's discontinued Ethernet/IP Capacity Tool can now be found inside of Integrated Architecture Builder (IAB.)
Note: To learn how you can get a free copy of IAB, check out my previous article HERE.
Then select, “Ethernet/IP Capacity Subsystem,” as shown below:
In this example I chose an L16:
After you select a Controller, if you put your mouse pointer over the question mark to the right side of your controller, you'll see a popup that lists your controller's specifications.
In the case of my controller, it shows the L16 only supports a total of four Ethernet Nodes:
Then I choose 1734 Point I/O, and enter a chassis count of two to indicate that I have two chassis with the same configuration.
Next I add the number of discrete and analog modules I intend to install, along with their RPIs, and then click on OK to add my I/O to the system:
Back in the main window I now click on “Compute” to calculate how much of my L16's “capacity” these two racks of Point IO use with the results are shown below:
Note: If you attempt to add more modules to a product than it supports, you'll see a red warning messages like the one shown below:
With my above errors corrected, I clicked on OK to close the I/O screen, and then clicked on the “Compute” button again.
Below you can see the results which show that I've exceeded my L16's max Ethernet Node count of 4:
After reducing my Flex I/O racks from three to two, I decided to add four PanelView Plus HMI's to the system, each with 1000 tags updating at 50ms:
When I recomputed the results, I found those four PanelView Plus's exceeded the L16's HMI “packets per second” (PPS) limit by a whopping 200%!
In an attempt to reduce the required HMI PPS, I changed the PanelView Plus update rate from 50ms to 100ms, and lowered the tag count to 800, both of which helped get my system under 100% utilization.
That said, there was very little bandwidth left, and I definitely wouldn't recommend designing a system with limits in the “yelllow” caution zone:
Note: While IAB does create each drop on the network, all the I/O modules used are the defaults, leaving it to the user to update them with the desired modules.
To watch a video of the above, check out Episode 52 of The Automation Minute Season Four below:
If you found this article helpful, please consider sharing it with your colleagues and on social media.
And if you'd like to post a comment or question on the above, just click on the “Click HERE to post a comment or question” link below.
Enjoy the benefits of membership! Patreon.com/automation
Check out my affordable courses: TheAutomationSchool.com
Ask me questions by clicking here to go to the comments link
Have an industrial automation news tip? Share it with us here
- SIMATIC Real-Time Locating Systems (P61) - September 9, 2020
- Using Siemens S7-1200 Signal Modules (S48) - September 3, 2020
- Air Amplification Technologies For Automation (P60) - September 2, 2020
Click HERE to scroll down to view or leave comments