In a previous article regarding ControlLogix processor faults, I mentioned one of the ways a processor can be faulted was by causing an array to go out of bounds when using an FFL and FFU instruction.
These instructions are commonly used to store multiple records at a given sample rate, which then can be averaged.
In today's article I'll walk you through setting the parameters of these instructions to do just that.
The first step is of the process is to record samples of your value or analog signal (level, temperature, pressure, etc) over a given amount of time.
We can accomplish this by using a Timer to trigger FFL and FFU instructions, and below I cover each of their parameters:
FFL (FIFO Load) Instruction Parameters:
Source – The signal or variable that you want to store in the array.
Generally, this would be a process variable like a weight scale, pH, or temperature.
FIFO – The Array in which to store the signal or variable.
In this example I'm using ACCArray with a DINT data type
Control – This can be any tag name with “CONTROL” as the data type.
Note that the corresponding “FFU” (FIFO Unload) instruction must use the same tag in its “Control” parameter so that they operate simultaneously.
Length – Length of the Array.
This is usually the same length as the Tag Array used in the FIFO parameter.
Position – Position to Load the Array
FFU (FIFO Unload) Instruction Parameters:
FIFO – The Array in which to Unload the variable.
In this example I'm using the same ACCArray with a DINT data type used above.
Destination – The variable that is being “Unloaded” from the array will be moved to this destination.
I chose a tag called “Trash” because I don’t need the variable once it has been unloaded.
Control – This can be any tag name and select “CONTROL” as the data type.
As noted above, the corresponding “FFL” instruction must use the same tag in its “Control” parameter so that they operate simultaneously.
Length – Length of the Array
Position – Position to Unload the Array
With the FFL and FFU covered, the next step is to use the AVG instruction to average the values we've collected and stored in our array, and below I'll detail the AVE's parameters:
AV (Average) Instruction Parameters:
Array – The Array which hold the values you wish to calculate an Average of
Dem. To Vary – The array's Dimension to use (0, 1, 2)
This parameter allows users with multi-dimensional arrays to select the dimension in the array to use (- ed.)
Destination – Where to place the Result of the Average Instruction. Consider this a “MOV” block inside the AVG instruction.
Control – This will be a CONTROL data type similar to the one used in the FFL and FFU instructions, but can not be the same tag as the FFL and FFU instructions. The AVG instruction needs to have its own dedicated CONTROL tag.
Length – The length of the array to AVERAGE.
In some situations you may only want or need to Average a part of the array, but it's more common to Average all of the stored variables.
Position – The offset into the selected array which the instruction is accessing.
This value is typically set initially to 0. (- ed.)
NOTES: Adjustments for sampling options:
- Make the array larger: Instead of only 16 stored data points as in this example, your array could be 50 points or more.
- Increase or decrease the timer preset to have faster or slower sampling: In this example I've adjusted the TIMER_LAB.PRESET to five hundred milliseconds, which results in the code sampling and store the signal value twice a second. Depending on what you are trying to accomplish, you may only need a sample every ten seconds, or you may need a sample every fifty milliseconds
The following is a snapshot of what your array will look like in the controller tag database:
The FFL and FFU instructions working together with and AVG instruction can give you great flexibility in adjusting the sample rate by simply adjusting the timer value that executes the instructions.
This is a real-life application that I have used many times for calculating weight signals and averaging the weight over several seconds.
If you are new to ControlLogix programming, hopefully you have picked up a tip or two here. If you take the time to learn each instruction, their parameters and use, then you will be setting yourself up for success in your automation and controls career.
Written by Brandon Cooper
Senior Controls Engineer and Freelance Writer
- SIMATIC HMI Basic Panel – Using the Recipe Feature - July 27, 2021
- TIA Portal Basic HMI Language Switching - July 15, 2021
- PanelView 800 Language Switching - July 14, 2021