In Today's article I walk you through how to Message data over Ethernet using the MSG instruction from a MicroLogix 1400 to a SLC-5/05 .
Note: In this example I have a MicroLogix 1400 at IP Address 192.168.1.66, and a SLC-5/05 at IP Address 192.168.1.47. Both have the same subnet address, and are attached to the same network via an Ethernet switch. Each program also had the N7 file expanded to 10 words, and the MicroLogix program has a free running Timer in Rung 0 of Program File 2 as seen below:
Step 6) Next I need to set how many “Elements” I'd like to send, starting from the previously chosen Data Table Address. In this example I chose a size of just 1 word.
Step 7) Now under Target Device I set the Data Table Address I want to write the data to in the target PLC, which in this example is also N7:0:
Step 8) The final setting I need to fill in on this tab that is the Routing Information File, which for this example I use file RI11:0:
Step 9) Now I navigate to the MultiHop tab:
Step 11) Back in Ladder File 2, I place an XIC in front of the MSG instruction. For the XIC instruction's address I use the Done Bit of my existing two second free running Timer. This will trigger the message every two seconds, a slow enough period that I'd be able to see the resulting status of each message attempt before the next message attempt is made:
Note: Since A-B Programmable Controllers have limited buffer space for MSG instructions, it's typically not recommended to have multiple unconditional MSG instructions in your program. Instead, consider interlocking messages or triggering them based on timers, to insure you never overfill your controller's message buffer. Doing so can also eliminate unwanted network traffic that unconditional / continuous Messages can generate.
Step 12) With my program now complete, I download it to my MicroLogix 1400 and run it.
Step 13) Now any value I enter into N7:0 in the MicroLogix 1400 is message to, and shows up in N7:0 in the SLC-5/05 after a short delay:
To watch a video demonstration of the above, check out Episode 43 of The Automation Minute Season 4 below:
If you found this article helpful, please share it with your colleagues on LinkedIn, Facebook, Twitter or Goggle Plus!
And if you know anyone who would benefit from Allen-Bradley PLC, HMI, or SCADA training, please let them know about my affordable courses over at TheAutomation School.
You can also share your own thoughts and opinions on this subject by clicking on the “post a comment or question” link below.
- Why Are My 5069-IF8 Analog Inputs Updating Slowly? - January 12, 2021
- First Look: Wago Pro 2 Power Supply - January 6, 2021
- Most Popular Rockwell Tech Notes Of 2020 - December 31, 2020